The 6 key points of the vacuum oil filter and the precautions for use法森
Vacuum oil filter instructions
1. Connect the oil pipe into and out of the oil pipe and close all valves;
2. Connect the three-phase four-wire power supply according to the total power of the machine. Click “vacuum open” to make the vacuum pump and oil pump turn in the same direction as the arrow. Connect the safety ground wire, check whether the circuits are connected reliably, and whether the oil circuit valves are open. The dynamic vacuum pump, the oil inlet pump and the oil discharge pump shall have no jamming and eccentric vibration. The model with a condenser can inject tap water into the water storage chamber through the drain valve, and the operation procedure is completed after the preparation is correct.
Vacuum oil filter manufacturers
3. Start the vacuum pump first. When the vacuum surface reaches the negative pressure -0.08MPa, the oil inlet valve can be opened to the oil until the oil in the vacuum tank reaches the neutral position of the oil mark. (Do not draw the oil into the vacuum pump, otherwise the equipment will not operate normally, if not When the oil is carefully sucked into the vacuum pump, the oil should be released from the vacuum pump in time, and then the appropriate vacuum oil should be added. After the oil drain valve is opened, the oil pump switch can be activated. The filter and regeneration function of the machine can be arbitrarily selected, as long as the ball valve can be switched. , began to drain oil and filter impurities to make the oil circuit cycle normally;
4. During normal operation, observe the oil mark tube to adjust the inlet valve to maintain the oil inlet and outlet balance, turn on the heater switch, set the temperature required to heat the oil, and volatilize the water in the oil. If there is more water in the oil, the vacuum tank When the oil foam will increase or the oil discharge pump is slow, the venting valve must be opened to control the vacuum. When the water is reduced, the oil level is lowered, or the oil pump is normal, adjust the bleed valve to stabilize the vacuum at 0.08. About MPa. At this time, pay attention to the reaction of each meter. If the pressure gauge reading is greater than 0.4 MPa, it indicates that too much impurities are adsorbed on the surface of the filter element in the fine filter, which needs to be cleaned and replaced.
5. Stop the heating system for 3 minutes when stopping, then stop the vacuum pump, (intake pump), close the inlet valve, and stop the oil pump after the residual oil is drained;
6. Open the bleed valve to bring the vacuum to normal atmospheric pressure, drain the oil in the cylinder, and release the remaining oil from the drain valve to prevent mixing into different types of oil for the next use, and finally turn off the air switch.